Frequently Asked Questions
Q: Why does the compressor not operate in heating mode?
A: The BULLDOG™ is an energy efficient hybrid heat pump which does not require compressor operation for heating. The BULLDOG™ unit utilizes a hydronic hot water coil for heating. The hot water can come from various sources such as heat rejected from other heat pumps operating in cooling mode, a boiler system, and/or a geothermal unit with our Compax Modular Chillers.
Q: What is the proper operating temperature?
A: The BULLDOG™ can safely operate in both cooling and/or heating mode with supply water temperatures from 85°F/30°C to 125°F/52°C.
Q: My thermostat is not bringing on the BULLDOG™ heat pump? This is one of the most common service issues.
A: The BULLDOG™ is a Hybrid Heat Pump and will not operate properly if the thermostat is set to “HP” (heat pump) mode. It must be programmed for electric or gas heating.
Q: Why does my BULLDOG™ heat pump take so long to start once the thermostat is calling?
A: Most programmable thermostats have an adjustable time delay (1-5 minutes) built into the thermostat program, and the BULLDOG™ heat pump has its own built in time delay of 10 minutes.
Home Owner Guide Home Owner Guide
Service Troubleshooting Guide Service Trouble Shooting Guide
Flash Code Diagnostics CGC BULLDOG FlashCode Diagnosis Table
Commission and Start Up
Commission and start up form Commission and start up form
If you have a question that is not listed above, please contact us and we will be more than happy to help!
For all service questions please forward them to: RWD@cgc-group.com